Legionnaires disease outbreaks, caused by Legionella in hospital drinking water, can be prevented using the right disinfection methods. Too often hospitals make treatment decisions on marketing claims not science. A research review paper, "Controlling Legionella in Hospital Drinking Water: An Evidence-Based Review of Disinfection Methods," published in Infection Control and Hospital Epidemiology, gives decision makers standard criteria to evaluate and choose the most effective Legionella disinfection methods for their facilities.
Legionella experts and authors Yusen E. Lin, PhD, MBA, of National Kaohsiung Normal University in Kaohsiung, Taiwan; Janet E. Stout, PhD, director of Special Pathogens Laboratory and from the University of Pittsburgh Swanson School of Engineering; and Victor L. Yu, MD, of the University of Pittsburgh, rate the efficacy of systemic disinfection, focal disinfection, and short-term disinfection methods used in outbreak situations. They offer a four-step approach to assist hospitals in choosing the most effective method.
Selecting the right method or combination of methods reduces the risk of patients contracting Legionnaires disease. Stout and her colleagues strongly recommend that infection control practitioners lead the environment of care team in choosing the best disinfection methodology. They also advocate for scheduled routine monitoring through culturing to ensure safe water.
"Hospitals relying on facilities managers and vendors in selecting a disinfection method may not be basing their decisions on evidence-based research. Our paper shows that some disinfection methods work better than others," says Stout, who along with Yu, discovered the link between Legionella pneumophila in hospital drinking water and hospital-acquired Legionnaires Disease in 1982 (http://www.legionella.org).
Common Legionella disinfection methods include: copper-silver ionization, chlorine dioxide, monochloramine, ultraviolet light, and hyperchlorination, (systemic disinfection); point-of-use filtration, (focal disinfection); superheat-and-flush with or without hyperchlorination (short-term disinfection methods in outbreak situations). Hyperchlorination or heat and flush are often used during an outbreak, but are the least effective. Copper-silver ionization has fulfilled the four-step criteria for demonstrating efficacy.
The authors four-step evaluation process of disinfection systems includes ensuring the technology kills Legionella. This step is followed by a review of anecdotal experience for controlling Legionella contamination in hospitals, followed by literature review of peer-reviewed and published reports of controlled studies of years of efficacy for hospital-acquired Legionnaires disease. Finally, to confirm with multiple hospitals that disinfection methods worked.
"We hope this review will assist hospitals in choosing a method that is safe, efficient and cost-effective," says Stout.